Specified in paragraph 5 of Article 16 of the Electricity Market Customer Service Regulation; "Those with installed power below 50 kVA consume inductive reactive energy in excess of thirty-three percent of the amount of active energy they consume, or if they consume capacitive reactive energy in excess of twenty percent of the active energy amount; those with installed power of 50 kVA and above are obliged to pay the cost of reactive energy consumption if they consume inductive reactive energy in excess of twenty percent of the amount of active energy they consume or give capacitive reactive energy to the system in excess of fifteen percent of the amount of active energy." (Rates can be changed by EPDK)
Therefore, the owners and managers of the facilities in accordance with the requirements of the regulation article; to build compensation facilities suitable for their facilities and to continuously monitor or maintain consumption; electricity bills will not have to pay a reactive price. Otherwise, they will have to pay high reactive energy costs relative to the rates instilled.
It's not just consumers; Electricity Distribution Companies will also have the opportunity to control the electricity bills they will pay to TETAŞ by comanzing their own facilities.
The main problem here is that the structure of the power structure in terms of electrical energy of the plant is thoroughly examined; appropriate compensation design and continuous monitoring.
Compensation Power State
First of all, by examining the power status of the facility to be compensation and preparing a design that can control reactive ratios; In addition to creating suitable products and groups according to the load and consumption status of the plant, practitioners who use as much domestic software as possible to manage this system should be preferred as well as the variety and quality of products to be used in the facility.
In addition to creating the ideal stage for many different consumption facilities by taking advantage of the data of the relay used within some of the companies that I have had the opportunity to examine for some time; in addition to being able to produce solutions with a smaller number of tripfaze codance levels instead of the large number of monafaze codances used in small loads in some facilities due to the properties of the relay used,
In addition to the 3 mA rated current of the relays, especially for the facilities that attract impact load, the response time is 20 ms, as well as the use of drivers with shute reactor tristors can be provided if necessary at the plant.
Remote control of established compensation facilities; results are delivered instantly to the facility manager or service server as sms messages in e-mail or mobile system, as well as providing full control, as well as gaining both time and workforce.
Otherwise, even if the most suitable compensation has been made for the plant; Compensation facility without consumption monitoring does not make sense alone! In any way, the condant, contactor or facility with the disabling of any fuse will have no meaning.
A reactive fee amount that you can pay on a monthly invoice may be several times the amount of the Compensation facility that you will set up in some cases based on the scale of your facility.
When you receive the reactive invoice, it is already in your second month invoice; your reactive consumption has increased, perhaps the second month will be too high to save the bill.
Therefore, it is the right way to establish a suitable compensation for the property, it should be noted that preventing is always cheaper than paying.